How to install the India AC power supply so that it can function as a protection switch?(2)
India The three-phase AC power intelligent protector has major electrical fault protection functions such as overvoltage, low voltage, neutral wire disconnection, short circuit, phase loss/opening, etc., and has fault identification, fault indication, voltage before closing, neutral live wire reverse connection, Zero line disconnection, phase loss/phase failure detection, remote monitoring, online parameter modification and software upgrade functions.
Remote control switch circuit
The remote control switch operation of the module power supply is carried out through the REM terminal. There are two general control methods:
(1) REM is connected to -VIN (reference ground), the remote control is turned off, and VREF<0.4V is required. REM is suspended or connected to +VIN, the module works, and VREM>1V is required.
(2) REM is connected to VIN, the remote control is turned off, and VREM<0.4V is required. REM is connected to +VIN, the module works, VREM>1V is required. REM is suspended, and the remote control is turned off, that is, the so-called "suspended shutdown" (-R).
If the control is to be isolated from the input, an optocoupler can be used to pass the control signal
The three-phase AC power intelligent protector has developed and created the function of "fault detection before closing", which has greatly improved its performance and reliability. The three-phase AC power intelligent protector detects the Marine boost/buck voltage power supply voltage, the reverse connection of the neutral line, the disconnection of the neutral line, and the lack of phase/phase failure through the single-chip microcomputer before the main switch is closed.